The photocell automatic setpoint calibration for nLight ADC does not turn lights off and back on again or does not appeart to work properly. The result is a setpoint of 5.0. If the setpoint calibration does not complete successfully, the setpoint will be defaulted. This failure may be caused by insufficient light to measure or possibly network communications error or setup incorrectly.
Check configuration of daylighting devices and dimming devices to ensure proper automatic dimming control is configured.
Try the automatic calibration process again, it may take an additional time before a measureable value is calibrated. Note: The process may take up to 30 seconds to complete.