Note: Not applicable to PCC1 card.
1. The device type for the PCC3 card on BUS MAP (or PANEL/SWITCH TYPES) must be set to "ANALOG/DIGITAL."
2. Pick an unused relay (or relay position) to be used as the enable/disable relay.
3. Assign the enable/disable relay to the trigger as specified on the table below. The trigger may be set to ON Mode or OFF Mode depending on the logic prefered. If the trigger is set to ON Mode, and the enable/disable relay is ON, the photocell will be enabled. If the trigger is set to OFF Mode, and the enable/disable relay is OFF, the photocell will be enabled (the enable/disable logic is in reverse compared to DE & AP Switches).
|To Enable/Disable Photocell Input #||Assign Enable/Disable Relay to Trigger #|
|Input 1||Trigger 11|
|Input 2||Trigger 12|
|Input 3||Trigger 13|
4. While the trigger mode (ON Mode or OFF Mode) is highlighted, press enter to access the sub menu. Change the settings as shown on the table below.
|To Enable/Disable Photocell Input #||Change the Settings To|
|Input 1 - Trigger 11||change to Digital 1|
|Input 2 - Trigger 12||change to Digital 2|
|Input 2 - Trigger 13||change to Digital 3|
When the input is enabled, the photocell reading will change relevant to the current ambient light level. In which, lights will turn ON if the level drops below the "on trigger."
When the input is disbled, the photocell reading will change to 1020 and will stay there regardless of current ambient light level. In which, the lights will turn OFF.