Yes, more than two SPODM 3X switches can be used to create a 4 way application. Similar to a 3-way application with the SPODM 3X, parallel the red, black, yellow, and yellow/black stripe wires. Use the white/blue stripe wire on ONE of the switches to the white wire on the power pack to control the relay, and cap off all other white/blue stripe wires. If a motion sensor is used, connect it to all white wires. If no motion sensor is used, connect the white wires to the red wires on the switch.
Have more questions? Submit a request