The nPP16 PL T24 was discontinued.
Its functionality can be replaced using an nPP20 PL BP.
Consider the nPP20 PL (that does NOT supply bus power) if customer wishes to ensure the bus does not stay powered if the lighting circuit drops out but the receptacle circuit remains active.
The nPP20 PL (BP) only tracks occupancy commands out of the box, ignoring switch and photocell commands by default.
Simply add this device into an nLight control zone with an occupancy sensor and the unit will automatically switch off when the room becomes vacant. Local manual switch and photocell control of receptacles is not typically required, therefore it is disabled by default.